The Hsinta and Nanpu Power Stations are located in southern Taiwan. The Hsinta Power Station consists of five combined-cycle gas turbines (CCGT), whereas the Nanpu Power Station consists of four. A project was undertaken to develop and deploy a predictive emissions monitoring system (PEMS) on CCGT unit 3 of Hsinta Power Station (HT-3) and CCGT unit 1 of Nanpu Power Station (NP-1) with the long-term goal of developing a universal model for this kind of power plant. After the first-year PEMS project at the Hsinta power plant, one goal of the second-year PEMS project was to set up a second PEMS at the Nanpu power plant and compare the PEM models applied the to two gas-fired combined cycle power generation units. Consequently, the second and third PEMS of Taiwan at CCGT HT-3 and NP-1 were finished. After comparing the differences among HT-1, HT-3, and NP-1 PEMS models, the pattern of model functionality indicated that this model could be applied to the other units of the same type and size. However, the PEMS function constant or parameter coefficients must be modified on a case-by-case basis. With regard to the PEMS model developed for HT-3, the relative accuracy (RA) of the 15-variable model with start-up mode is only 7.43% and met the criteria of draft PS-16. With regard to the PEMS model developed for NP-1, the RA of the 10-variable model with start-up mode was only 7.76% and also met the criteria of draft PS-16.
|頁（從 - 到）||907-913|
|期刊||Journal of the Air and Waste Management Association|
|出版狀態||Published - 2010 八月|
All Science Journal Classification (ASJC) codes
- Waste Management and Disposal
- Management, Monitoring, Policy and Law